افزایش ثبات سیستم های چند ماشینه با استفاده از بازبست تطبیقی خطوط انتقال
|کد مقاله||سال انتشار||مقاله انگلیسی||ترجمه فارسی||تعداد کلمات|
|54469||2014||7 صفحه PDF||سفارش دهید||3981 کلمه|
Publisher : Elsevier - Science Direct (الزویر - ساینس دایرکت)
Journal : International Journal of Electrical Power & Energy Systems, Volume 62, November 2014, Pages 391–397
When a fault occurs in high voltage (HV) and Extra High Voltage (EHV) lines, they could automatically be re-entered to the circuit by auto-reclosing operation of transmission switches after passing a certain time from the first tripping operation. It is due to the fact that most of the faults occurred in HV/EHV transmission systems have a corresponding arc which could be removed just after de-energizing the line. To ensure successful reclosing, de-energizing interval addressed as dead time is conventionally determined, based on the calculation of the time needed for quenching subsequent weakened secondary arc. However, on-fault reclosing is probable even if dead time is conservatively selected. It can lead to severe power swings and put the system in danger of instability especially in vastly loaded networks. These swings will be intensified or weakened upon rotor angular speeds of dominant generators in reclosing instant, which is the key factor in acceleration or deceleration of power swing. Therefore power oscillation can be mitigated by adaptive selection of dead time. In this paper, a new method for dead time calculation is proposed in order to mitigate power oscillations effectively. The proposed method can also be implemented in on-line monitoring and control algorithms due to low amount of calculation. In this approach, single machine infinite bus equivalent (SIME) method is used for the evaluation of power oscillations.