مدل حرارتی کف سالن هاکی روی یخ مناسب برای کل سازه تجزیه و تحلیل شبیه سازی انرژی
|کد مقاله||سال انتشار||تعداد صفحات مقاله انگلیسی||ترجمه فارسی|
|10522||2011||7 صفحه PDF||سفارش دهید|
نسخه انگلیسی مقاله همین الان قابل دانلود است.
هزینه ترجمه مقاله بر اساس تعداد کلمات مقاله انگلیسی محاسبه می شود.
این مقاله تقریباً شامل 4745 کلمه می باشد.
هزینه ترجمه مقاله توسط مترجمان با تجربه، طبق جدول زیر محاسبه می شود:
|شرح||تعرفه ترجمه||زمان تحویل||جمع هزینه|
|ترجمه تخصصی - سرعت عادی||هر کلمه 90 تومان||8 روز بعد از پرداخت||427,050 تومان|
|ترجمه تخصصی - سرعت فوری||هر کلمه 180 تومان||4 روز بعد از پرداخت||854,100 تومان|
Publisher : Elsevier - Science Direct (الزویر - ساینس دایرکت)
Journal : Building and Environment, Volume 46, Issue 5, May 2011, Pages 1087–1093
This paper presents a thermal model for an ice rink floor system that is integrated into EnergyPlus, a whole-building energy simulation tool, to improve design, evaluation, and operation of ice rink facilities. The developed ice rink floor thermal model, based on the conduction transfer function method, is validated against experimental data obtained under laboratory testing conditions. Two control strategies for indoor ice rink floor systems were modeled and evaluated including a brine temperature control strategy and an ice surface temperature control strategy.
Ice rink arenas are among the most energy intensive entertainment facilities with annual energy consumption of 750 kWh/m2, almost 3 times the energy use intensity of office buildings . There are several thousands of indoor ice rinks in North America used for various spectator events and recreational activities such as hockey games, figure skating, or public skating. Most of the arenas are operated continuously for over 8 months to 11 months per year and thus consume significant levels of energy when compared to other recreational facilities. According to a DOE report, a typical indoor ice rink arena in Massachusetts had an average electric consumption of 730 MWh which accounted for $70,500 in 2010 for just a 7–8 months season . Another study showed that the energy costs to operate an ice rink facility in Canada for 8 months are on average $86,000 . According to the international ice hockey technical guides, the energy consumption by three ice skating rinks in Europe ranges from 900 to 1500 MWh/year and the average energy bill can range from $50,000 to $90,000 . Unfortunately, there is no clear guidelines and analysis tools to help improve the energy performance of ice rinks. In particular, it is difficult to estimate refrigeration load and energy use of ice rinks using currently available whole-building energy simulations due to lack of detailed models for ice rink floor systems. Early numerical and experimental analysis studies of indoor ice rink arenas were usually focused on indoor air quality . Recently, ASHRAE has sponsored a research project to better estimate ice sheet cooling loads . In particular, a numerical analysis was performed as part of this project to estimate daily heat flux profiles at the ice sheet surface under steady and periodic meteorological conditions  and . As an extension of this ASHRAE project, a zonal model is developed to calculate thermal interactions between indoor air and ice sheet surface within an ice rink arena. This zonal model is used with TRNSYS to estimate annual energy consumption for ice arenas ,  and . However, the model is a standalone algorithm and cannot be easily implemented in a whole-building simulation program. The main objective of the work presented in this paper, is to develop a detailed heat transfer model for a typical ice rink floor suitable for integration within a whole-building simulation tool. While existing models , , , ,  and  can estimate heat transfer along the ice sheet surface, they do not consider thermal coupling of the ice rink floor system with its surroundings. In this paper, a thermal model for the ice rink floor system is developed to account for thermal interactions between the floor system, ground, and ambient air of the indoor arena. Moreover, the developed ice rink floor system model was integrated into a state-of-the art energy analysis simulation program, EnergyPlus, to assess energy performance of ice rink facilities under various design and operating conditions.
نتیجه گیری انگلیسی
A thermal model for ice rink floor system was developed and integrated within EnergyPlus. The thermal model uses the conduction transfer function (CTF) method to calculate long-term energy consumption of ice rink floor system. Two control strategies for indoor ice rink floor systems were modeled and evaluated including: brine temperature control and ice surface temperature control. The predictions of the ice rink floor system model integrated within EnergyPlus were validated against measured data obtained for a small scale ice rink arena testing under laboratory conditions. Good agreement between the simulation model predictions and measurements were found for all the ice rink floor insulation configurations. The thermal ice rink floor system model presented in this paper, integrated within whole-building simulation tools, can provide designers and professionals with a valuable tool to better design and operate ice rink arenas.