تجزیه و تحلیل عملکرد از چیلر های جذبی ظرفیت کوچک با استفاده از روش مدل سازی های مختلف
|تعداد صفحات مقاله انگلیسی
|9 صفحه PDF
نسخه انگلیسی مقاله همین الان قابل دانلود است.
هزینه ترجمه مقاله بر اساس تعداد کلمات مقاله انگلیسی محاسبه می شود.
این مقاله تقریباً شامل 5930 کلمه می باشد.
هزینه ترجمه مقاله توسط مترجمان با تجربه، طبق جدول زیر محاسبه می شود:
Publisher : Elsevier - Science Direct (الزویر - ساینس دایرکت)
Journal : Applied Thermal Engineering, Volume 58, Issues 1–2, September 2013, Pages 305–313
This paper presents a review and comparison of simple, yet accurate steady-state models of small capacity absorption chillers using highly reliable experimental data obtained with an absorption chiller of 12 kW in a state-of-the-art test bench. These models can potentially be used in complete modeling and simulation tools or in supervisory control strategies for air-conditioning systems using absorption chillers. With respect to that, a comparative evaluation of different modeling methods for predicting the absorption chiller performance is presented. Four empirically based models: the adapted Gordon-Ng model (GNA), the characteristic equation model (ΔΔt′), the multivariable polynomial model (MPR) and the artificial neural networks model (ANN) were applied using the experimental data and thoroughly examined. The paper also presents statistical indicators and tests which might assist in selection of the most appropriate model. The excellent statistical indicators such as coefficient of determination (>0.99) and coefficient of variation (<5%) clearly indicate that it is possible to develop highly accurate empirical models by using only the variables of external water circuits as model input parameters.
The main aim of this paper is to present a comparative evaluation of different modeling approaches for predicting the performance of small absorption chillers. The comparative evaluation can serve as a reference when there is a need for simple, but accurate models of absorption chillers, for example to integrate these models in complete energy supply and demand models included in simulation software packages. These simple chiller models, characterized by a low number of input parameters, can serve to facilitate the annual simulations of complex building systems providing at the same time an adequate level of performance prediction. Also, this paper aims to provide a statistical approach which may help in selecting the appropriate model. With respect to absorption chiller modeling, both physical and empirical approaches were many times presented in the literature. Physical or more precise thermodynamic models were reported by many authors. Here just a brief review of the most recent or relevant will be given. Grossman and Zaltash  developed a modular simulation tool for absorption systems called ABSIM. With this software is possible to study various absorption cycle configurations using different working fluids. ABSIM calculates the cycle internal state points and thermal loads in each component using a cycle configuration build by the user graphically and for given working fluid specifications and operating conditions. This is enabled through the governing equations for each component of the cycle contained in the software subroutines. However, the calculation convergence is not always easy. Silverio and Figueiredo  used a thermodynamic approach for steady-state simulation of an ammonia-water absorption system. The thermodynamic state relations, the pressure drop equations and the heat transfer coefficients were solved by using an algorithm based on the Substitution Newton Rapshon method. Kaynakli and Kilic  performed a theoretical study on the performance of a H2O–LiBr absorption system using a thermodynamic analysis of the absorption cycle. These authors investigated the influences of the driving temperature and heat exchanger effectiveness on the thermal loads of the components and COP. Yin et al.  developed a detailed thermodynamic model of a 16 kW double-stage H2O–LiBr absorption chiller. The steady-state model was based on the working fluids property relations, detailed mass and energy balances, and the heat and mass transfer relationships for each chiller component. One of the most recent application of the thermodynamic approach in absorption system modeling can be found in the paper of Wu et al. . The authors developed thermodynamic models of different absorption heat pump cycles to test their applicability with different heat sources, working pairs and in different cold regions. All these thermodynamic models are very demanding since they require comprehensive knowledge of the absorption cycle including some internal state points. These models need lots of input parameters such as heat transfer coefficients (U) and heat transfer areas (A) of heat exchangers, the rich solution flow rate, working fluid properties and water side flows and temperatures as well as some additional assumptions for the convenience of modeling. A more complete explanation on all these degrees of freedom in the modeling of absorption chillers can be found in Dereje et al. . In practice, however, especially with commercial units, the internal parameters are not available. This is the reason why thermodynamic models are more adequate during the design stage of absorption equipment as explained in the paper of Florides et al. . Also, the computation time in simulation software packages using these models is very long since they require a lot of simultaneous iterations. The annual simulation of absorption chillers under different ambient and operating conditions on an hourly time step basis is a clear example of this. Thus, there is a need for simple models which can provide sufficiently good representation of the absorption machine behavior based only on available external parameters (experimental measurements or manufacturer catalog data). Simple models can be more easily incorporated in simulation programs or used for fault detection and control. Contrary to the physical models, the empirical and semi-empirical models require less time and effort to develop and computation time is much shorter when they are built into complete energy management simulation programs. The parameters and fitting coefficients in these models are determined by using a regression method or a minimization algorithm applied to a dataset obtained performing experimental measurements or using a manufacturer catalog. The studies about development of empirically based models for absorption chillers have been reported by several authors. Gordon and Ng  developed a general model for predicting the absorption chillers performance. The model lays both on physical and empirical principles. The physical principles that govern the performance of the absorption chiller are fitted to the experimental or manufacturer data by using a regression method. Ziegler et al.  and  developed a model (Characteristic equation method) which predicts the performance of the absorption chiller by using two simple algebraic equations: one to calculate the cooling capacity and another for the driving heat input. These two previous models belong to semi-empirical (gray-box) category of models, in which the fitted parameters can be interpreted under the actual physical principles which govern the absorption chiller performance. Labus et al.  used a completely empirical approach to model absorption chillers based on manufacturers curves in order to investigate the energy savings when different absorption chiller configurations were considered for their integration in a complete chiller plant. The Artificial neural networks approach has been also used for absorption chiller modeling. ANN models belong to the black-box model category, that unlike gray-box models, the estimated parameters of the model have no physical interpretation. Sözen  used the ANN to determine thermodynamic properties of an alternative working pair for absorption systems. The study also demonstrated that ANN can replace mathematical models in the simulation of absorption systems. In the paper of Sözen and Akçayol  the ANN approach was proposed for performance analysis of an absorption chiller. The ANN model used only the working temperatures in the four main components as input parameters in order to predict the performance of the chiller. Manohar et al.  applied ANN for the modeling of steam fired double effect absorption chiller. Later, a similar work was carried out by Rosiek and Batlles , who used ANN to model solar-assisted air conditioning system with hot water driven double effect absorption chiller. The last approach considered in this paper is the simple multivariable polynomial regression which also belongs to the black-box category of models. Regardless the numerous studies on the modeling of absorption equipment, literature review shows that there is a lack of information with respect to comprehensive comparative studies on different modeling techniques for predicting absorption equipment performance in a similar way as Swider  or Lee et al.  did for the case of vapor-compression chillers. The main aim of this paper is to present a comparative evaluation of different modeling approaches for predicting the performance of absorption systems. In the next section are presented the experimental data and a brief description of the evaluated types of models. Later the application of these models to the experimental data is evaluated with the help of statistical indicators and statistical tests to select the best modeling approach.
نتیجه گیری انگلیسی
A comprehensive comparison of different methods for steady-state modeling of small capacity absorption chillers was presented in this paper. Four models were developed based on experimental data. The models were based only on the measurements of the external water circuits. Statistical indicators such as R2 and CV showed that GNA model has the lowest predictive capacity. Although the GNA model could not reproduce the chiller performance with high accuracy, it is still used in some cases due to its simplicity. This is justified by a fact that on a whole year hourly simulation, these deviations will most probably equal out to a great extent. However, the statistical analysis indicates that would be more appropriate to use one of the other three methods in order to obtain better accuracy. Excellent statistical indicators (R2 around 0.99, CV lower than 5% and narrow CI) clearly show that any of the three methods (ΔΔt′, MPR and ANN) is suitable for the performance prediction of absorption systems, and could be used for the chiller control and monitoring, fault detection or optimization. Nevertheless, the best prediction was obtained with the ANN method with R2 > 0.998 and CV<2%. The comparison of the models with AICc and BIC statistical tests confirmed that ANN was the most suitable method to model the selected absorption chiller.