عملکرد مخازن ذوب صنعتی در تهیه پاسخ فرکانس پویا در سیستم قدرت بریتانیا
|کد مقاله||سال انتشار||تعداد صفحات مقاله انگلیسی||ترجمه فارسی|
|161729||2017||12 صفحه PDF||سفارش دهید|
نسخه انگلیسی مقاله همین الان قابل دانلود است.
هزینه ترجمه مقاله بر اساس تعداد کلمات مقاله انگلیسی محاسبه می شود.
این مقاله تقریباً شامل 7766 کلمه می باشد.
هزینه ترجمه مقاله توسط مترجمان با تجربه، طبق جدول زیر محاسبه می شود:
Publisher : Elsevier - Science Direct (الزویر - ساینس دایرکت)
Journal : Applied Energy, Volume 201, 1 September 2017, Pages 245-256
As a result of the increasing integration of Renewable Energy Source (RES), maintenance of the balance between supply and demand in the power system is more challenging because of RESâs intermittency and uncontrollability. The smart control of demand is able to contribute to the balance by providing the grid frequency response. This paper uses the industrial Melting Pot (MP) loads as an example. A thermodynamic model depicting the physical characteristics of MPs was firstly developed based on field measurements carried out by Open Energi. A distributed control was applied to each MP which dynamically changes the aggregated power consumption of MPs in proportion to changes in grid frequency while maintaining the primary heating function of each MP. An aggregation of individual MP models equipped with the control was integrated with the Great Britain (GB) power system models. Case studies verified that the aggregated MPs are able to provide frequency response to the power system. The response from MPs is similar but faster than the conventional generators and therefore contributes to the reduction of carbon emissions by replacing the spinning reserve capacity of fossil-fuel generators. Through the reviews of the present balancing services in the GB power system, with the proposed frequency control strategy, the Firm Frequency Response service is most beneficial at present for demand aggregators to tender for. All studies have been conducted in partnership between Cardiff University, Open Energi London â Demand Aggregator, and National Grid â System Operator in GB to ensure the quality and compliance of results.